How to Read a Pump Curve

If you buy or use industrial or municipal pumps, you need to be able to read a pump curve.  A pump curve is a detailed spreadsheet of a pump’s performance at specific intervals, the use of which helps you determine the configuration and type of pump you need for your application. It’s like looking at the product details of a light bulb in comparison to your electrical socket and lighting needs. We are going to look at the various intervals and measurements that you need to consider in order to make the best decision for your application.

Overview

The graph shown here is where a pump curve is usually charted.  Keep in mind that not all manufacturer’s pump curves will look the same, but they will follow these general principals. It is best to start by defining what the X and Y axis are measuring:

The X Axis (Horizontal Line) gives the Flow Rate.  On this graph, it’s recorded as Gallons Per Minute (GPM) and Cubic Meters per Hour (M³/H). The Y Axis (Vertical Line) gives the discharge pressure measured in Feet of Head – how far the fluid will travel given ZERO friction losses.

As we take a closer look at pump curves, it is important to note that the viscosity of the fluid will change the curve entirely.  The viscosity of liquids change when the temperature changes.  For this curve, I am using room temperature water as the fluid being pumped.  For pumping purposes, you want to measure the Dynamic Viscosity of the fluid since it is moving.  At 70°, water has a Dynamic Viscosity of 975 mPa-s (Millipascals/second), and that is the viscosity of the fluid outlined in the Pump Curve I am showing today.  The easy part is done.  Now, we dive a little deeper into what all the different lines in the middle of chart are.

Efficiency

When looking at a Pump Curve, you always want to find the conditions under which the pump will operate at its best.  In the “Efficiency Graph,” you can see several curves with numbers labeling, in percentages, where the pump’s efficiency will be at the various flow rates.  When you look at this specific pump’s efficiency curve in the graph, you want to look at the area in between the curve labeled 77, because that is where it will perform its best.

Based on the efficiency curves in the efficiency graph, you can expect this particular pump to be able to generate ~650–850 GPM at ~55–70 Ft of Head at its best.  However, this does not mean that pump can only operate within those parameters.  Indeed, this pump can operate between the lowest efficiency, 45 percent, to right-most side of the 70 percent curve without any vibration caused by cavitation.

If you want to pump ~ 950 GPM at ~48 ft. head, then this pump will work well for you at about 70% efficiency.  It is when you deviate outside of the represented curves that you run into problems.  If you want to pump 1000 GPM at any head, then you will need to seek a different pump, because the pump will constantly cavitate and fail quickly.  It all boils down to what your application needs are; reading the efficiency curves is the best place to start when checking a pump curve.

Impeller Size

Impeller size is one of the easiest ways for an engineer to manipulate the flow rate.  That is why having a curve that shows how an impeller operates at various sizes is helpful to the engineer when considering a pump’s use for a specific application.

In the graph, you can see that we have added the impeller curves in red.  Based on this pump’s efficiency curves and the impeller curves, it is safe to say that you can order this pump with an impeller size between 12 and 13 inches and still be within 77%efficiency.  Let’s look at the graph another way.  Say you want to pump 500gpm with, at least, 50 ft head, then you will want an 11in impeller, because it will yield it’s highest efficiency.  If you need to pump 400gpm with 45 ft head, then you have some options. You will notice that the 70 percent efficiency curve lines right up with 400gpm with an impeller diameter between 10in and 11in. With only this information, it might be easy to say, “I can probably choose any size in between those numbers,” but there are still more curves to be considered.

Horsepower Requirements

The horsepower requirements for the flow you want to achieve combined with the impeller diameter is laid out in the associated chart.  The horsepower curve is outlined in green.  It is recommended that the motor selected have 1.2x more horsepower than is required for the flow rate of the application.

For example, if your application needs 400gpm at a rate of 52 ft of head, then you will want to bump up to a 10hp motor.  This protects you motor from failing when loads on the pump increase unintentionally.  However, a 10hp motor without a Variable Frequency Drive (VFD) exceeds the power necessary to pump 400gpm at 52 ft of head, and the impeller will need to be trimmed to a little less than 11in for the pump to operate within the application’s parameters.

When the horsepower, impeller size, and efficiency curves are combined it will give you a good idea what size impeller and motor you will need to pump your product and how efficient the pump will be at pumping that product.  To take the example from before: if you want to pump 400gpm at 52 ft of head, then your pump’s specs will be the following:

•   ~ 10.8in size impeller

•   10 horsepower motor

•   Pump Efficiency ~ 70%